Nearly 80 lawmakers have signed onto a bill that would require public schools in Massachusetts to test their water pipes for lead. The bill also...
Although it is considered "conventional" in many parts of the world, membrane technology is beginning to get serious attention by U.S. water suppliers as one of the newest treatment alternatives for high-quality drinking water production. The interest is well-deserved as water suppliers grapple with layer upon layer of water supply issues. As with any technology-and especially those with limited U.S. application to serve as reference-keen interest must be balanced with prudence. When it comes to drinking water, there is no room for technologies that don't deliver results. And, when it comes to spending public money, there is little tolerance for "innovations" that carry excessive price tags.
Over the past couple of years, several water suppliers in the U.S. have selected membrane technology for new or upgraded water systems Although each system inevitably is confronted by individual conditions, one water supplier-Plantation, Florida, which relies on wells for its source-faced issues that are familiar to water suppliers around the country. The work of the city and its consultant, Metcalf & Eddy, to address those interconnected issues illustrates the factors that must be considered and accommodated in the selection of a membrane treatment process. Not surprisingly, those factors begin with the water supply and end at the tap.
The nominal capacity of the treatment system was 13 MGD. With actual production during the past three years between 2 and 6 mgd, the East Plant was relegated to serving as a peaking facility for Plantation's water system, which centered on the recently-renovated Central Treatment Plant.
The broad issues facing the city were not uncommon: deteriorated equipment, increased service demand, and heightened treatment requirements inflicted by new or anticipated Safe Drinking Water Act (SDWA) controls on pathogens and disinfection/disinfection by-products (D/DBP). Technical choices available ranged from replacing existing equipment with upgraded lime softening to employing membrane softening. Potential upgrades to the lime-softening system included incorporating ozonation, activated carbon, ultraviolet irradiation, or a combination of those. Based on earlier experience with membrane technology at its Central Treatment Plant, Plantation initiated a program to upgrade the East Treatment Plant using membrane technology. A need for flexibility and cost-efficiency fueled the decision to develop all the support facilities that would be required for the full build out of a 12 mgd facility, but to limit initial installation of new membrane treatment units to those required for 6 mgd production capacity initially. Until the new system was operable, the existing lime-softening system and all essential support systems had to remain in service.
The city's utility director, Mel Entus, wanted to use as much of the existing system as possible in the new design. Still, the new reverse osmosis (RO) softening system selected required a new building with approximately 16,000 sq ft of floor space on one level. Constructing this facility required the demolition of the north Dorr-Oliver treatment unit, the washwater recovery basin, the lime sludge lagoon, the sludge thickener, the vacuum filter, and the sludge-dewatering building. The demolition, in turn, required the use of a temporary lime sludge lagoon and backwash recovery basin to maintain the Infilco lime-softening system in service. The 5-mgd Dorr-Oliver unit was converted for sludge storage and the 0.6 million gallon storage tank was assigned to backwash recovery.
Unlike many selection processes where the optimal treatment technology is the result of extensive evaluations of alternative technologies, Plantation's upgrading project began with deciding on a scheme capable of achieving very high treatment levels. Targeting reverse osmosis was not the last step in the process; rather, it was Plantation's first step, based on previous experiences with RO. And, like any first step, the effects and needs triggered by Plantation's decisions extended far beyond the treatment process.
Jay Ameno, M&E Project Director, explained, "Many people are familiar with the fouling potential of membrane systems and of the effect raw water quality will have on that potential. What is less often recognized, though, is the expected effect of an RO system on withdrawal capacity or the interdependence of the treatment and supply facilities. Assessing the water supply system goes far beyond identifying raw water quality parameters."
In fact, the assessment extended beyond gathering water quality data, both chemical and biological, to include the following: configuration of original wells, materials of construction, pumps, piping, valving, electrical components, geology, hydrogeology, capacity, well efficiency, sand and colloidal material, maintenance history, age and life expectancy of wells, and permitted capacity. After each well was investigated, the wellfield and the raw water transmission system as a whole required evaluation.
Water Quality: The nature of membrane softening triggers particular concern over raw water quality because of the potential for membrane biofouling. Identifying the source and type of any biological contamination also was critical here in assessing the potential remediation of wells or the wellfield. Seven of the ten wells serving the East Plant are located within approximately 50 ft of the East Holloway canal. Under current regulations issued by the Florida Department of Environmental Protection (FDEP), the South Florida Water Management District (SFWMD), and Broward County, these wells would not be permitted because of that proximity. The canal, which acts as a source of recharge, could have a hydraulic connection to the wells, with the possibility of biological contamination from a surface water source. Exacerbating that possibility is the Miami Limestone Formation, a very porous formation through which the canal is cut. Finally, the species of biological contaminant was of critical concern, not only for well protection, but also for the protection of the cartridge filters and membranes.
Supply System: The existing supply system showed signs of deterioration. Some well pumps showed leaking packing glands, which allowed the development of algal, bacteriologic and fungal growths on the outside of the wells. One pump bowl assembly, which had been left on the pad of a well, showed severe corrosion, indicating galvanic incompatibility between the water and well materials. In addition, concerns about water hammer arose. This could possibly cause silting and sanding problems, and even contamination from the nearby canal.
Based on the analysis, the newest existing 1 mgd well was to be modified, and joined by seven new 2.4 mgd wells with 100 hp submersible, stainless steel pumps to provide a minimum pressure in the 50p;60 psi range in the RO feed-pump suction header. The new wells are approximately 150 ft deep, cased for the first 110 ft with a 24-in. diameter, 1-in thick PVC casing. The open hole portion has the ability to have a stainless steel screen installed if required, according to project hydrogeologist G. M. Witt.
Permitting: Groundwater withdrawals in Broward County are controlled by two regulatory agencies: SFWMD, which regulates the quantity of water that can be withdrawn by any individual entity from a given area and issues FDEP permits for well construction, repair and abandonment; and Broward County, which controls the placement of wells and wellfields through the county's Wellfield Protection Ordinance.
The Plantation utility already had a consumptive use permit for its wellfield but several other permitting issues emerged.
First, the city's SFWMD permit, with an expiration date of June 10, 1998, had a 1995 permitted allocation of 4.451 billion gallons per year, with a maximum daily allocation of 16.33 million gallons. For 1998, the allocation shows a 21 percent increase, for an annual withdrawal of 5.631 billion gallons a year. Although this is adequate to meet projected service demands, an RO system would be expected to show a loss of approximately 15 percent of the supply as concentrate, or brine. To obtain the 12 mgd of finished water required by the city from the East Plant, 14 mgd of raw water is needed.
Plantation considered several options for concentrate disposal. Discharging directly into the ocean was unlikely, so consideration shifted to tapping into an existing ocean outfall. However, the nearest outfall systems are located at least 12 miles away from the treatment plant. Other surface water disposal possibilities included the withdrawal of canal water from the East Holloway Canal, mixing the concentrate with the canal water, and discharging the mixture back into the North New River Canal; or, mixing the concentrate with the canal water and incorporating it into a reuse system.
Deep well injection is a viable alternative when surface water discharges are not feasible due to such conditions as receiving water body acceptability, source availability, or regulatory constraints. Because of its classification as an industrial waste, RO concentrate requires a Class I injection well for disposal, defined by the FDEP as a well used to inject hazardous waste beneath the lower-most formation containing an underground source of drinking water within one quarter mile of the well bore.
A Class I well requires certain subsurface conditions, including a highly permeable injection zone that has been classified by the FDEP as suitable for waste injection. In southeast Florida, the Lower Oldsmar Formation, or Boulder Zone, has been used successfully as an injection zone. To protect the potable and potentially potable water supplies of the Biscayne and Floridan aquifers, brine concentrate disposal wells have to be constructed with approximately seven strings of casing in various diameters. Each casing string must be completely cemented in place, with the exception of the pit casing and the monitor zones of the intermediate casing, using API Class H cement and lost circulation additives to ensure a good bond. The final selection of casing depths, monitor zones, and injection zones depends on information collected during the drilling, sampling, and testing of a mandatory pilot hole.
Although Plantation was using an RO concentrate injection well at the Central Water Treatment Plant, the geology at that site differed significantly from the geology at the East Plant's proposed injection well site -just as the raw water feeding the two plants differed.
Because of the city's successful experience with the Central Plant, which had been upgraded with a membrane system, Plantation's interest in using similar technology at the East Plant was understandable. Yet, different considerations affected selection of the appropriate solution for each facility, precluding a "twin" design.
Three major differences deserve mention. First, the Central plant had an existing wellfield designed around lime softening, whereas the East plant has a wellfield developed specifically for membrane processing. Second, lime facilities at the East plant were in good condition, allowing conversion from quicklime to hydrated lime for pH and alkalinity control. This change enables the East plant to produce a stable finished water, reducing the need for much additional treatment for scale prevention or corrosion control. Third, a wider selection of membranes is available now than at the time the Central Plant was upgraded with a membrane system.
Despite these broad differences, there was considerable interest in maintaining reasonable uniformity between the membrane softening systems at the two plants, which led to Metcalf & Eddy's development of an upgrade design for the East Plant that shared as many characteristics as possible with the Central facility. Among these were the size and capacity of the membrane modules (standard 8-in. diameter by 40-in. spiral wound membrane modules with 360 sq ft or more of effective surface area); the pretreatment equipment (depth-type, plain-end, 40 in. polyethylene cartridge filter elements in industrial style housings located ahead of the membrane softening arrays); and the Allen-Bradley programmable logic controller hardware and software.
The similarities between the two systems were accompanied by significant differences, based on the different design considerations of the two plants. For example:
Just a few miles away, in Hollywood, Florida, a completely different system, also designed by Eddy, was built. That city's original water supply, like that of Plantation, was the Biscayne aquifer, but a growing population demanded additional supplies. Because of the withdrawal limits imposed on Southeast Florida water users, the city was forced to seek out new water supplies to supplement its existing allotment from the Biscayne Aquifer. The Floridan Aquifer, a deeper and poorer-quality source, proved adequate in quantity. Since the city's existing lime-softening equipment had reached the end of its expected lifespan and was incapable of meeting upcoming SDWA regulations, Hollywood set about developing a new system.
The design response in that community was vastly different from that in Plantation, involving two separate treatment trains to augment the existing lime-softening system. The first new section used nanofiltration, while the second train (reserved for use on the poor-quality Floridan Aquifer water) employed reverse osmosis. The more "obvious" design response to the two-source raw water supply would have been to combine the flow from the two sources and subject it to one treatment process. In the case of the combined Biscayne and Floridan water, that single treatment process would have been reverse osmosis, which is the most intensive method-and usually the most expensive. Instead, the designers chose to treat each separate raw water supply according to its specific needs, and then to blend the finished water prior to distribution for a uniform taste and odor. The innovative, parallel treatment response produced considerable savings for the client and ensured that the finished water would be virtually indistinguishable from that previously provided by the city's lime-softening system.
Because membrane technology is relatively new in the United States, especially for drinking water applications other than desalination, many water suppliers are unfamiliar with the intricacies of membrane design and application. That unfamiliarity is counteracted by an understandable interest in the technology, based on its ability to address such critical drinking water issues as pathogen and D/DBP control. It deserves note that the technology's promise as the treatment technology of choice for many water utilities must be balanced with a recognition that its application is site-specific, dependent on variables that include raw water quality, required treatment levels, existing infrastructure, disposal methods, and cost.
In fact, "membrane technology" is not a single product or system, but a category of systems, processes, materials and products. The four primary types of membrane technology-ultrafiltration, microfiltration, nanofiltration and reverse-osmosis (also called hyperfiltration)-are available in a variety of configurations and materials of construction. Any specific membrane type may or may not require pretreated water. The selection of the wrong type, configuration, or material for any individual application is likely to trigger problems ranging from frequent fouling to unacceptable removal efficiencies.
It is because of these variables that membrane technologies-perhaps more than treatment techniques with which we in the U.S. are more familiar-virtually demand front-end testing in bench-scale, pilot-scale, or both. Without doubt, membranes represent a significant advance in drinking water technology and are likely to play a growing role in the U.S. water industry. When properly selected, designed and installed, they outperform many conventional processes and virtually eliminate the potential for pathogen breakthrough. But, as with any technology employed in the unforgiving business of providing safe drinking water-and as those of us in the industry realize on a day-to-day basis -the success of any individual application rests as much on the capabilities of the designers as on the structure of the equipment and facilities: the "thinking" is as critical as the "constructing."