Water Quality Deterioration in Distribution Systems: Part 1
Recognition of the Role of Microorganisms
Beginning over a century ago, studies have been conducted to address the broad range of drinking water quality problems that originate in water distribution systems. Many of these problems involve the growth of microorganisms that may contribute to the formation of accumulations on pipe surfaces, create unwanted tastes and odors, consume disinfectant residuals or accelerate corrosion.
Much of the pioneering work of leaders in the waterworks profession has been lost or clouded by the veil of antiquity. Still, most of the remedial measures in general use today originated from their observations or were originally recommendations of these leaders. This series is an attempt to recreate and refresh the images of those whose work has led to our current understanding of microbially-mediated corrosion and water quality deterioration during distribution.
of Microbial Growths
The involvement of microorganisms in water quality deterioration during transmission was noticed very early in the history of water supply. Leeds (1897)1 reported that problems of "taste and odor" affecting the Brooklyn, N.Y., water supply were related to bacterial growths in the distribution system. Subsequently, other early investigators also related the development of tastes and odors to microbial growth.2, 3, 4
In order to confirm the diverse, sporadic reports of microbial regrowth in water distribution systems, Powell (1921)5 surveyed 32 municipal water systems and found that 92 percent had reported increases in the number of bacteria at the consumer’s tap. In addition, the quality of water at the tap showed signs of degradation.
Addressing problems related to microbial growths in the Baltimore, Md., drinking water supply, Baylis (1922)2 observed a wide variety of organisms including algae, diatoms, protozoa and bacteria in the distribution system. He expressed concern for the lack of attention being given to microbial growths in water systems. Noting a significant increase in bacterial concentrations in winter months, he concluded that decaying algae and diatoms penetrating the distribution system had provided nutrients for "scavenger" bacteria. Even at this early date, Baylis was apparently aware that microbiotic cycling of nutrients between algae, diatom and bacteria took place within water distribution systems. He concluded that taste and odor problems may have been caused by both algal byproducts and subsequent bacterial growth.
Similarly, Kofoid (1923)3 attributed the development of tastes and odors to the growth of algae in reservoirs. He emphasized the maintenance of high quality source water to mitigate distribution system problems.
Transmission of Disease
The principal concern over the observed increases in the number of microorganisms during distribution was related to fear of disease transmission. Reflecting this concern, a Committee on Water Supply established by the Public Health Engineering Section of the American Public Health Association (1929)6 reported, on the basis of a survey, that a number of cities exhibited severe bacterial aftergrowths in their distribution systems.
Schaut (1929)7 attributed high bacterial growth in the Philadelphia, Pa., water system to cold water temperature when chlorination was least efficient. The fact that organisms in polluted river water were penetrating treatment barriers in the winter underscored concern over the potential for disease transmission.
The first experiments to evaluate the control of "bacterial aftergrowths" were conducted by Baylis (1930)8 utilizing two parallel, continuously-flowing taps. Significant aftergrowths were observed where the pipe system received unchlorinated water, while low bacterial plate counts were observed when a 0.5g Cl/m3 (0.5 ppm) chlorine residual was maintained.
Observing high counts of B. coli in the sediments deposited in pipes, Baylis concluded that pipe sediment accumulations interfere with the destruction of bacteria even though the water may contain high levels of chlorine. Reasoning that there would be regions of chlorine-free water within the sediment in which bacteria could grow abundantly, he recommended that a systematic flushing of dead-end water mains was necessary to control bacterial activity and maintain disinfectant residuals in a distribution system.
Shannon and Wallace (1944)9 sampled the water supply system of Detroit, Mich., and isolated 495 bacterial colonies. Samples were taken of the chlorinated water plant effluent, at distribution system dead-ends and in consumer complaint areas. Forty-two of the colonies isolated were Gram positive cocci; five were Gram positive rods and 448 (91 percent) were Gram negative rods. Of the 448 Gram negative rods, 32.5 percent were of the coliform group, 20.5 percent Alcaligenes, 12.7 percent Pseudomonas, 12.3 percent Proteus, 9.5 percent Eberthella, 4.4 percent Salmonella and 6.9 percent unidentified species. The researchers postulated that either these bacteria had survived chlorine disinfection or were recruited during distribution through system defects such as main breaks, back-siphonage and cross-connections.
Alexander (1944)10 emphasized the importance of maintaining chlorine residuals throughout a distribution system in order to control the development of slime-forming (attached) organisms on pipe surfaces. Even if introducing a "sterile" finished water, he hypothesized that organism growth within a distribution system could be only partially controlled. In addition, Alexander recognized the presence and effects of diverse microbial interrelationships. He observed Bacillus, Sarcina, Micrococcus, Flavobacterium, Achromobacter, Alcaligenes, Pseudomonas and Proteus genera in distributed water. Based on his observations, he suggested that the source water was the principal factor in determining the organisms subsequently found in the distribution system.
Alexander concluded, "that because of the new U.S. Public Health Service requirement of distribution system sampling, many water works men are just beginning to find out what we have known for many years, that is, that all kinds of growing organisms will thrive in the distribution pipe systems though an apparently perfect water has been produced at the plant."
Microbial Growth and Predation, Red Water and Tubercle Formation
Based on a long-term study of Boston Water Works surface water reservoirs and two distribution system locations, Whipple (1897)11 reported decreases in organism densities during distribution. He examined tubercles as well as a large, thick brownish mat removed from a section of water main removed from service. The brownish mat was identified as the sponge Polyzoa. Whipple hypothesized that bacterial densities had declined during distribution due to cell sedimentation and "decomposition," or consumption by the Polyzoa specie. This observation introduced the complication of predation in assessing changes in bacterial populations during distribution.
Shortly after the identification of Crenothrix polyspora in water distribution piping by E.G. Smith (1903),12 O.T. Smith (1904)13 reported a case study at Freeport, Ill., where yellowish-brown solids were identified as a Crenothrix species. Since water flushed from system dead-ends exhibited very high total iron concentrations, main flushing was proposed as a remedial measure.
A succession of investigators14—23 addressed the range of problems related to the transformation of iron by bacteria. The causes, costs and measures for control of corrosion, red water, tubercle formation and loss of hydraulic capacity were systematically addressed. Chlorination, the use of chemical "sequestering" agents and systematic main flushing were recommended control measures.
Baylis (1926)15 conducted original, scientific studies to determine the role of bacteria in iron corrosion and tubercle formation. He determined that, whereas the pH of the distributed water was 7.9, the pH within a microbially-active tubercle was about 6.0. In a "dormant" tubercle, the pH ranged from 6.4 to 6.8. Moreover, chloride and sulfate ions were concentrated inside active tubercles. Baylis also determined that the black, columnar, porous fibers formed within the tubercle were magnetic ferrous-ferric oxides. The predominant iron-precipitating bacteria in the tubercles were identified as Gallionella, Crenothrix, Clonothrix, Leptothrix and Sphaerotilus. Subsequently, Olsen and Szybalski (1949)24 conducted studies that showed sterile water did not cause tubercle formation whereas water containing Leptothrix caused both accelerated iron corrosion and tubercle formation.
Repeatedly, filamentous iron bacteria became associated with red water, foul-tasting water and loss of pipeline hydraulic capacity. Wilson (1950)25 described "water calamities" in California caused by accumulations of Crenothrix. A three-year program of chlorination and flushing was required to remediate the problems. San Francisco’s Hetchy tunnels lost as much as 20 percent of their carrying capacity to surface accumulations of gelatinous, light-brown slime growths.26 Palo Alto received more than 1,200 red water complaints attributed to Crenothrix.27 Although they found no relation to iron concentrations, Lueschow and Mackenthun (1962)28 detected Gallionella and Leptothrix in 35 Wisconsin well waters.
While various species of Eubacteriales were found to precipitate iron, Hyphomicrobium and Gallionella species have been most commonly associated with manganese deposits in water pipelines.29—32 Clonothrix and Crenothrix species were found capable of precipitating both iron and manganese oxides.
Wolfe (1960)33 observed large sheathed bacteria that concentrated iron and manganese in their sheaths from a water supply containing no detectable manganese and less than 0.02g Fe/m3 of iron. Hairlike aggregations in dark gray-brown flocculent clumps were identified as Clonothrix putealis. Dried deposits were found to contain 69 percent organic matter, 10 percent ferric oxide, 12 percent manganese oxide, 9 percent silicon oxlde and 0.08 percent phosphate. Wolfe concluded that sessile organisms can concentrate iron and manganese from dilute suspensions of metals.
Alternately, saprophytic, slime-forming bacteria were reported to have caused a 10 percent decrease in hydraulic carrying capacity in a 2.4 meter diameter main.25 In Santa Rosa, Calif.,34 the use of well water resulted in prolific growths of non-filamentous bacteria. These bacteria formed heavy accumulations of brown to gray-to-black slime and caused severe discoloration and septic odors. Dissolved oxygen was completely depleted within 15 minutes of contact with distribution system piping. The application of 3g Cl/m3, followed by main flushing, reportedly alleviated the problem within three weeks.
The corrosion of iron during distribution is of special importance because the generation of ferrous ion results in the reduction of chlorine and chloramine residuals. With the loss of these bacteriostatic agents, both microbial growth and iron corrosion rates increase.35, 36
In 1964, Mulder reviewed the behavior of slime-forming bacteria and summarized information on the isolation, cultivation and ecology of iron bacteria. Miller and Litsky (1976)37 classified bacteria found in natural waters and distribution systems as sheathed higher bacteria, stalk or caulobacteria, the spiral forms, the pigmented and non-pigmented rods, the cocci, the nitrogen-fixing and nitrifying bacteria. Touvinen (1980, 1982)38, 39 recovered a wide range of organisms from tubercles in the Columbus, Ohio, distribution system. These included sulfate reducers, nitrate reducers, nitrite oxidizers, ammonium ion oxidizers and sulfur oxidizers as well as various unidentified heterotrophic microorganisms. By this time, it was clear that distribution systems routinely serve as hosts to an exceptionally large and diverse population of microorganisms.
Confirming and extending the work of Baylis (1922),2 Wilson (1945)26 suggested that bacteria originating in source waters penetrated treatment facilities and, thereafter, became attached to pipe walls. Microbial colonization resulted in the formation of surface slimes and, ultimately, in the formation of encrusting tubercles. Because of extensive microbial growth on pipe surfaces and within tubercles, he concluded that it would be impossible to accurately enumerate all the bacteria present in the distribution system.
Wilson was among the first to articulate the concept of microbial ecology within a drinking water distribution system. He suggested that the types and numbers of bacteria that develop in a water distribution system depend on the ecological niches available. He also recognized that many organisms that are unable to flourish in a particular environment may survive in a dormant state for indefinite periods. Subsequently, with a change to a less inhibitory environment, the dormant organisms may again become active, particularly in response to seasonal temperature changes. He suggested that different symbiotic microbial forms become active from season to season and place to place within a single water distribution system.
Wilson also contributed to the early understanding of the microbially-mediated transformation of iron, manganese, sulfur, carbon, nitrogen and phosphorus compounds by a mixed population of bacteria, fungi and protozoans. With respect to bacterial growth at distributed water temperature, he reported higher colony counts on plates incubated at 20° C than on plates incubated at 35° C.
Noting aesthetic concerns resulting from the formation of taste-and-odor-producing compounds during water distribution, Wilson cited Beggiatoa, Thiobacillus, Crenothrix and sulfate-reducing bacteria among those responsible for aesthetic degradation, corrosion of pipes and the production of tubercles.
From the wide range of investigations conducted by early investigators, distribution system problems have long been associated with microbial growths. The changes investigated included
• precipitation and agglomeration of iron and manganese precipitates,
• chemical changes resulting from the activity of nitrifying and heterotrophic organisms,
• tastes and odors originating from sulfate reduction or organic metabolites,
• biologically-mediated corrosion and tubercle formation,
• bacterial involvement in deposition and accumulation of materials on pipe walls, and
• the reduction in flow rates due to tuberculation, slime growths and depositions on pipe walls.
By mid-century, the scientific underpinnings of the microbial processes leading to water quality deterioration had been clearly articulated. In addition, these early researchers identified both the organisms involved and the methods of control most commonly used today. Many articulated the need for maintaining a bacteriostatic disinfectant residual to control the adverse